My plumber fitted a new (very nice) shower that requires a 40 amp supply onto the existing wiring which is 30 amp, after 10 minutes under the shower it will cut out as the fuse trips (and is v.hot). I like the new shower and don't want a less powerful one. It is on 6 mm cabling and is directly connected through a wlex box that has 30 amp written on it. What I want to know is if I buy a replacement fuse for this box that is rated 40 amp will it work as required.
hi matt its sounds as if u have installed a shower with a rating of over 8.5 kw can u check? if it is over 9 kw u will have to replace the 6mm twin earth cable with 10 mm and have a 40 amp fuse please dont be tempted just replacing the fuse of the fire risks darryl
THIS OPERATION REQUIRES CERTIFICATION BY AN ELECTRICIAN QUALIFIED TO DO SO UNDER PART P OF THE BUILDING REGULATIONS.
It wasn't over 8.5 kw but the cable was buried in plaster and maybe in a cavity wall for a long stretch so maybe that is why it was running warm. I just didn't feel comfortable with it so we've now got it running on a more modern 32 amp mcp and it seems fine now the shower does not cut off even after 1/2 an hours full power shower! Thanks for the feedback as unless I had actually felt the wire myself I would have left it as a 45 amp mcp which may have been a little dangerous I guess.
You can check online for a chart that tells u the size of cable to use for the size of shower and the length of the cable run.All showers i wire these days i run a 10mm cable although i had to buy a shower to run of a 30amp mcb with 6mm cable that was existing.i just used the chart and it works fine and is within the load that is suitable.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!