Here's a question. Recently had garage converted - all pukker and above board.
The new room now has eight light fittings - four on each side of the ceiling, all energy savers.
The 'spark' on the job wired all eight back to a 1 - gang switch. I'd now like a 2 - gang switch, meaning that I can switch off one bank of four. Given that all the wiring has been done, plastered and 'finished', what can I do to make the change I require?
The 'spark' says it cannot de done without a rewire.