hi i want to add a new rad in my conservatory how do i find out if my combi bolier will be able to take it its a fairly new combi about 3yrs olds iv looked on the boiler for info but it all makes no sense to me
if u tell me what make and model of boiler you have and measure the lenth and depth of all your radiators i can work out how big a radiator can be installed. Also let me know which are single panel, double panel or p+.
Hi Rambo sorry for the delay in getting back to you i forgot that i asked for the dimensions and not many people actually come back to a post but here gos
Your boiler is the rsf (room Sealed Flue) I hope as you said it was the 28cdi this has an output on the central heating side of
9-24kW (30,700-82,000 Btu/hr)
The size of your radiators have a btu size of (give or take 10 btus)
2: 1000x600 3519 each total 7038
1: 480x600 1759
2: 400x600 1408
1: 1440x450 not sure but roughly 4500
2: 960x460 3021 each 6042
you have just under 21000 btus used so the boiler should be sufficient as the radiator you want to hang is only 3737 btus
So long as the pipework is not too long the boiler should cope well enough.