I had a new hot water tank fitted a few weeks ago.
On start up in the morning now there is a lot of air moving around the system.
same in afternoon startup
Its not the Rads I have bled them. the air can be heard in the hot water heater.
Why would this happen weeks after fitting?
How can I cure this as it seems to be getting worse.
I hope someone out ther can help
When you say the hot water heater do you mean the new cylinder? If so have a look at it. There should be two pipes going into it, one directly above the other, on one side. These are the feed and return pipes between the boiler and the heating coil inside the cylinder.
You may be lucky with it being new. A bleed off point, like a radiator bleed valve, might have been fitted on the higher one of these pipes near where it enters the cylinder. If not, try loosening the joint on the higher pipe on the side of the cylinder. This should allow any air trapped in the coil to be released. When only water is dripping out, retighten the joint.
Alternatively, get the people who fitted it back to sort it out at their expense. They shouldn't have left it with air in the system.
I imagine that the hot water entry point on the copper cylinder is the highest point on your central heating?
One way to deal with this is to add a T into the top pipe and to fit an air vent. Screwfix have one Quote No: 97868 Pack Prices (inc. VAT) Quantity 1 £4.35
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!