hoping you may be able to help me with a problem on my vented heating system ...
to cut a long story short
i have relocated my hot water cylinder and pump in the attic (to liberate space on the landing ... airing cupboard)
in order to do this I have lifted both the storage tank and the central heating expansion tank about 1.5m in order to provide the necessary head on the hot water cylinder and keep the expansion tank above the pump ... maintaining a positive presuure throughout all the system.
the problem i have is that my system is continuously filling up with air, rads require bleeding and the system is noisy (assume it is the air)
i think i am drawing air in through the vent to the expansion tank when the pump starts ... the length of the vent pipe is less than it was originally and i do get overflow from the expanion tank which seems to coincide with the pump starting
i have overcome the problem by selecting a lower speed on the pump, unfortunately at a lower speed i do not seem to be able to balance the system such that all the rads heat up ... no matter how much i try.
currently in the 22mm vent line there is a simple air separator, vessel
i was wondering if anybody knows of anything on the market which i can put in the vent which will prevent air being drawn in.
i was looking at mechanical air vents/separators and backflow prevention products ...
This problem can occur wherever the tank is and is due in part to a poorly designed system. Ok, so by moving the tank it has made it worse, but the root cause is the same.
If the heating filling pipe is enters the loop at a different place to the expansion pipe, particularly if they are on either side of the pump, air can be sucked into the system, or in the opposite case, water forced out of the expansion.
Re-position either pipe so there is no opportunity for this pressure differential to cause a problem. Put the expansion on the highest part of the system, and the feed a foot or two lower in the same pipe. Consider when redesigning, that the expansion must allow for steam to escape if the water was ever to boil.
You may find a similar problem when filling a bath say, that air is drawn down the expansion on the DHW side too!
It is best to put the expansion pipe as close to the top of the boiler feed as possible so if the water were to boil, the steam would find an easy way out. Then put the feed pipe close by and lower down if possible, but not more than a foot or two away.
This would guarantee regardless of whether the expansion is under vacuum or pressure, the feed is going to be the same.
According to my copy of the Hot and Cold water supply regulations, The system should have an......."open safety vent to permit escape of steam in the event of system overheating (and) should not be fitted with check valve or other obstruction".
Frankly, I think you are on dangerous ground here. You may recall someone was killed last year by an exploding backboiler where steam was trapped and unable to escape. If the one way valve was ever to seize shut................
Really the only way to resolve this properly is to move the feed pipe to a better location.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!