i have an ideal isar HE 30 boiler, when i turn the thermastat down on the living room wall to frost stat, then try to turn it up again the boiler does not fire up, the same happens with the hot water (combi boiler)
i have to go into the shed the status is flashig F then L when i press the reset the number 5 appears then C then D.then it is ok until i turn the stat down again. any help gladly appriciated
If you left the room thermostat alone would the boiler work day after day without going to lockout ?
Codes L - F means that the boiler has attempted to light 3 times and failed. So it could be a problem with the PCB, igniton, flame sensing electrode/lead or gas valve. With the fault being linked to the room stat I would imagine the fault would be with the PCB.
It'll probably be best to get an engineer out to take a look.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!