hi there, i have replaced a vokera combi with a ferroli DOMIcondens f. the system has 2 zones, upstairs and downstairs working from indipendent room stats and motorised valves. the new boiler needs to have volt free room stats. will these work the motorised valves? also will the existing wiring do? thanks.
Without changing anything else it only requires a 230v relay fitting at the boiler end of the existing 'Call for heat' signal wire & Neutral.
Using the Common & Normally open contact terminals connected to the boilers 'volt free' stat. terminals.
Any competent electrician should be able to do this.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!