In the original wiring I have one red permanent live, 2 red loop wires, 1 black neutral, and 2 earth wires twisted together. In the new light fitting I only have the normal 3 terminals, live neutral and earth. I first of all wired the new light, in the normal way, but left out the 2 loop wires. The light stays on, and won't turn off at the switch, I have tried all sorts of combinations with no success. Where DO the loop wires go? Help!
Permanent line is one of the loop wires which will connect to other loop wire and not to lamp.
The switch wire should connect to the lamp with the neutral.
The loop wires don't go anywhere just connect together.
http://www.ericpalmer.fsnet.co.uk/Lighting.html shows a number of diagrams as to how connected as does the projects section does this help?
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!