I want to change the existing ceiling light fitting in the kitchen and replace it with a ceiling bar with 3 spotlights.
When I removed the current light filtting (which has 2 bulbs inside) from the ceiling rose I found 2 brown and 2 blue wires (one brown going into each bulb respectively). The new ceiling bar I purchased requires only one live feed and one neutral. what do I do with the spare live wire and the neutral??
Firstly turn off the power to this lighting circuit at the fuse board
Using the connector block supplied with the light fitting, connect both brown wires to the live terminal and both blue wires to the neutral terminal, ensure connections are tight
You don't mention any earth wires ?
Unless your new fitting states it is "Double Insulated" or carries the symbol of a square inside another square, it MUST be earthed
Hopefully the 2 earth wires are there and in which case, simply connect to the earth terminal on the fitting, ensuring that these wires are sleeved with green/yellow sleeving
Hope that this helps and let us know how you get on
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!