Hi, Firstly may Wish everbody the best for the new year.
There are some cold spots on downstairs rads around the bottom middle area of them. Could anybody give me advise how to quickly solve my problem.
Boiler is BIASI RIVA COMPACT HE, M96.24SM/C2.
Thanks for help
if they are cold at the bottom and warm at the top its a sure sign that there is sludge in the system. try adding sludge remover to the system, via the header tank is best if you have one. and you could remove the affected radiators, drain and flush with a hosepipe then put them back on, this will help shift some of the muck although there could still be lots gunk in the pipes.
if this fails to do the trick then its probably going to require an expensive power flush, you need to consult a local plumber about this.
Thank's for advise. I had a feeling that's what it was. Just had new boiler fitted over Christmas (I've been away for a holiday). The plumber has not flushed the system through (I called and asked him) He's coming to finish the job this week, says it was best to let it run for a while.
Much appreciated for quality advise, have a Happy New Year
The plumber you employed doesn't sound like 'one of the good ones'. Yes the system should be left to run for abit, with descaler or sludge remover added - WITH THE OLD BOILER CONNECTED.
Now your new boiler will be full of sludge, debri etc. If it's not flushed cleansed and inhibitors added (quickly) your boiler warranty is void. And something will probably pack up within 1 - 2 years.
Get him back and give him a chance to do it. Should take a good few hours. He should drain and fill the system 2 or 3 times. Whilst the system is cold and hot. Also ask to see the cleanser and inhibitors he's added.
There's normally stickers on the bottles where he would write the date he added it, and stick this on the boiler case.
Hi htg engineer,
Thanks for advise, plumber coming around tomorrow! there is a tub full of inhibitor that he has left, so i'm guessing he intends using that. Now i'm concerned about the damage that could be happening to the boiler. I do know the plumber and comes with good recomondation and reputation.
But I will be asking questions.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!