Just had a combi boiler installed (Glow worm 30cxi) and now I need to drain the central heating system so that I can move a radiator. So my question is, once the heating system is drained can I continue to use the boiler to supply hot water to the taps or do I need to turn off this hot water supply as well?
Have tried searching other questions on this forum for the answer, but no joy so far. Very grateful for any info.
hi tonyfu if you drain the system you wont be able to carry on using it as the boiler needs to hav 1 to 1.5 bar pressure to operate correctly and if you were to try and fire your boiler up after you drain it it cud crack the heat exchanger then your talking big money to fix it hope this helps bazza ps are you sure its a combi not a condensing boiler as it is illegal to fit combi boilers now