I will be installing a 4.5kw double oven in a couple of weeks.
I already have 10 metres of 6sq mm cable most of which will be needed to install by the "clipped direct method"from the fusebox via the 45amp socket to the cooker and a spare 32amp mcb .
Would you consider both the 6sq mm cable and the 32amp fuse to be oversized or can they be safely used anyway?
Am i right in assuming that "clipped direct method" means securing cable to the joists by plastic clips?
As a new user of your site I find your publications most useful-thank you.