We had a new kitchen put in recently and all the electrics had to be rewired as they were pretty old and not up to current regulations. They did however leave some of them exposed.
I want to get tiling and am not sure on the best way to cover them up, the boxes don't seem to be a regulation size for anything I've seen at a hardware store.
your electrician should have done this there strict regulations concerning electrical installation in kitchens. Has your electrician signed this work off yet as it must comply to part p of building regulations.
If the cables are not buried at least 50mm from the surface of the wall (thats both side of wall!)
Then the cables should run in the vertical and horizontal safe zones this means that cables should run at direct right angles of each other in the vertical and horizontal plain of switches or socket-outlets, or within 150mm from top of wall and 150mm of ajoining angles of walls or be protected from mechanical damage by using either metal conduit or metal plate coverings.
Hope not too confusing but this is important, If you are unsure of anything I have mentioned, I will try to explain better.
Try get your electrician back to finish his work off correctly.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!