I just replaced two light fittings in my bedroom cupboards both on the same light circuit. The new fittings have an earth terminal on them which I connected up OK. The first one works fine but the other one throws the circuit breaker out as soon as I energise the light circuit. If I disconnect the earth wire to it though it then works fine.
Has anyone any clues as to why it won't work with the earth connected?
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!