Just tried to put some inhibitor into my combi boiler via the filling loop. Checked the connections and the only place the adaptor nut (that goes onto the can) would fit it just prior to the non-return valve (ie without using the actual loop). It went in fine, but when I tried to take the nut off the one way valve didn't seem to work and every where got sprayed with my can of X100!!! I managed to get the filling look back on but not before it had sprayed over the boiler plug and fuse, which has now short-circuited the system and the boiler now does not have power to it.
Where did I go wrong? I checked I was filling it in the direction of the arrow on the non-return valve, and I checked which pipe was which (ie cold water mains inlet and boiler loop). Did I just have a dodgy non-return valve, and if so I guess I need to drain the system to fit a new one.
jmh (covered in X100 inhibitor and not pleased with herself!!)
It sounds as though you didn't take the pressure of the system!
In any event its much easier to put it in via a radiator, take the pressure off the system, remove the blanking plug on the opposite end to the bleed valve, fit a ½" BSP elbow and pour it in. Replace the blanking plug, repressurise and off you go.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!