I rent out a property and every year I am required to obtain a landlords 'gas cerificate'....this is arranged by my letting agent.
This year they changed their 'gas' company and now I've received notice of some remedial work that is advised to be done!!
The following observations have been pointed out by the new company....(and yet these have never been reported previously).......namely that the 'free standing gas cooker' should be attached to a safety chain....and that the 'bayonet fitting' should be facing down!!!!
Your professional comments on this subject will be greatly appreciated as the company concerned want £100 to rectify what I (as a non pro;) consider to be expensive for the work advised.
The new company observations are probably correct. Whether their proposed charges are reasonable will depend on your location - if you are in london or miles from anywhere expect to pay more.
Hi guys...stoneyboy and htg engineer....
Your replies answer my question....thanks!!.....now heres another!!!!!!!!!!
I'm in the process of getting three quotes for fitting a new 'Condenser Boiler' in my own house (Bungalow) .
So far I've had two Gas Fitters visit and both have different views on the discharge of water that might emit from the 'pressure relief valve'.
One says that the water from this valve can be direct in to the 'stench pipe'....whilst the other says that the pipe should be directed through an external wall so that it can be seen to drip if the valve is activated.
Also one has mentioned the condenser pipe discharge and the other one has not mentioned it.
Which is correct....it'll be interesting to hear the views of the third fitter due to visit this Sunday'
Sorry for what might seem to be a rather 'gaggle' on my part, but as Gas Engineers I'm sure you know what I'm on about!!!!!!!!!!!