After an extension my gas meter is in now in my garage is this allowed?
It was outside and council signed off building after extension. It has been like this for ten years but man came to change meter and would not touch it.
If your gas supply to the meter is by plastic pipe, very likely as it was outside, then the instalation does not now meet current regulations.
The plastic supply pipe must not be inside a building due to it not meeting the fire resistance regulations.
The cost of re-piping the supply form outside to your meter in steel pipe or moving the meter to the outside will be down to you I am afraid.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!