Hi people Wounder if you could help with this please. I'm wiring up 3 seperate lights in a workshop to a 3 gang switch. So each pole on the switch turns each ligth on, so i can have one light on or two or all 3 lights on. My question is in this unusual scenario im I right in thinking i dont have a switch live so no need for a blue sleeving? I can have the live of supply to the common on switch one and linkied througth to common on the other two switches. and the line coming in from the 3 lights going to L1 on each switch With the CPC and neutral waggod together? Ill try and attach a photo. AM I CORRECT any advice please
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!