Hi, hoping you can help. I have hot water venting (through the vent pipe) into my central heating header tank in the loft. If I turn the CH pump down to setting 1, this does not happen, but as soon as I switch to 2 or 3, it does.
I have used a CH cleaner that I put in the system and left for a week. I then drained the system and refilled it, putting in some inhibitor as well. I thought all was well as the system was not venting when on pump setting 2. But no surprises, later that evening it started venting again.
Logic says to me that there may be a blockage somewhere, but I need to be clear, my plumbing capabilities are minimal bordering on zero.
What would you suggest and will leaving it in this state for any length of time cause me bigger problems?
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!