which of the 3 black wires from the cables for my light fitting is the SWITCH LIVE.
I have 3 reds. 3 Earths and 3 blacks...of which i believe 2 should be neutral and one a switch live.
a step by step type intstruction guide would really be appreciated.
I wish i had a Quid for every time this one crops up....
You should have marked the black on it's own before disconnecting, presume changing light so three reds go to spare loop-in connector, not to fitting.
two blacks together go to neutral of fitting & remaining black, after marking as red with tape etc goes to fittings live connection.. earths together to fittings earth.
if disconnected and blacks not identified some times sw.line black will have been 'doubled over' or neutral blacks may have been twisted together before and you can tell by close inspection, (power off).
if still not sure, with circuit dead connect a meter on ohms range to the 3 reds together and the other wire to each black in turn whilst turning switch on/off/on untill meter responds to show the switch line black, mark it with red tape and see above.
if no meter avail. a battery/bulb/buzzer will do,
If still stumped Get Someone In.....best wishes SPARX
Cheers Sparx...got me multimeter on it and found the switch live..all the lights work now but one of them seems to take its time coming on....but better late than never as the saying goes.
Much appreciated sparx.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!