I want to swap some horrible flo tubes in a cricket pavilion lounge area for recessed 50w downlighters.
I normally work on the 240v x 6a = 1440w for a circuit rule. However I want to fit roughly 30 spots in this room, along with 3 or 4 wall lights. This would mean over 1600w, and would mean 2 circuits by my rule.
How does it affect the ruling if 12v downlighters were installed rather than 240v? I only ask because there is not a spare way in the consumer unit and it's a question of economics for the club.
Thanks in advance, Dickie