I'm running 16m of 6mm2 armoured cable from consumer unit to a new 40-amp double pole cooker switch in kitchen. Q1 Do I then run cable from switch to cooker outlet(load).??? Q2 There is no room for a new 32 amp breaker so i'm fitting an enclosure breaker. To connect this what and how??. L N E into enclosure breaker loop out into Consumer Unit L goes Where???? N to NETURAL and E to EARTH??????????
Please help ASAP :idea:
Problem is this is notifiable work, as I am assuming the location is within a kitchen?
So should be notified to building controls, it's a legal requirement.
To cut a long story short, by the time you have paid fees for a diy job, be cheaper to call an electrician.
Why are you running SWA cable?
The C.U is in the hall. I have to drill a hole to feed the cable (SWA) outside, clip it along the side of house. Then drill another hole and feed the cable to the new cooker switch that is located in the kitchen. So i should just call an electrician?????????
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!