You still give very little information but I can make a few comments.
1) To take a supply from the consumer unit will require notification under Part P and the LABC charge so much over £100 it is not really worth doing it DIY you may as well get an electrician who is a member of a scheme and can sign it off himself.
2) Any rotating machine needs some protection so if turned on and there is a power cut it does not re-start when power comes back. Easy way would be to use an "ACTIVE" RCD these drop out when there is a power cut.
3) Starting single phase machines can require special starters and extra power to start it. Motors with brushes have very different controls to squirrel cage motors and some of the starters can be very expensive but double as both MCB and Starter. It can use capacitors, and/or centrifugal switches and you may need type C or D MCB's to allow it to start. Because of this the ELI (Earth loop impedance) may need to be very low so heavier cables may be required.
As I have said the information is not enough to really give an answer but since likely it will be cheaper to employ an electrician seems pointless anyway.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!