My ideal minimiser se condensing boiler stalls several times after coming on in the mornings (burner light off but the fan keeps running) before staying on any length of time, it also bangs very loudly sometimes before stalling. 3 engineers have looked at this under the insurance and so far have cleaned the flue thoroughly, replaced the probes and the gas valve which made no difference. The last engineer figured out that the boiler runs perfectly with the cover off, which I tested over a weekend and confirmed the same. So must be something to do with gas/air mix? They are now out of ideas and I am concerned the insurance will say it is beyond ecomomical repair. Anyone have any ideas.
This boiler can be very toublesome especially if the heat exchnager is not cleaned regularly. However as you have had several engineers look at the problem I would suggest you replace the ignition unit. In my experience this component starts to produce a weak spark after a few years which can lead to explosive ignition.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!