i am thinking of having a spa bath fitted, how must the pump be wired/protection of circuit and do i need a part p electrician. Was thinking of spurring of the ring main into 3 amp fused spur and then to pullswich with neon
With the new 17th edition of wiring regs now in place, this type of installation now needs to be protected by a 30ma RCD.
Plus it should by law be done by a part p qualified electrician.
The way you are considering to do the circuit up untill July 1st 2008 would seem to be okay, but now the 17th edition is requiring circuits in bathrooms to be on a seperate one to any other circuit in the property.
This is as a safety issue as the human body is more vunerable to electric shocks within the bathroom enviroment and if a electrical fault to earth did occur the RCD would trip and the elecrical supply would disconnected.
I hope this info was of help.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!