Hi, upstairs is wrong,
the red not from the 3core does not go in with the other one , it goes in L2 with yel. there is also another black core loose in the box which goes in with L1 blue.
Have just read bit abt bathroom sw. now i'm confused!!!
you were talking abt stairs light?????
Is landing sw a 2gang (double?)
not enough cores to make any sense......
pls have another look in box for 'spare' cores & reply thanks,
Hi agn. if you take the 'spare' red out of the bathroom sw.
a) does bathroom light still work.
b) has landing light gone off?
If both yes, then think back to when you changed sw. was there a wire looped between the bathroom & landing switches?
If there might have been then your 'spare wire' goes in L2, & a link wire needs to go from landing sw. L1 to bathroom sw. red live in.
If you find the landing light only works when bathroom sw. is on then the link needs moving to the other term of bathroom sw. ie on side of bathroom sw. is perm L & other side is sw-L & you need to feed landing light from perm L side,
Hope this makes some sense......
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!