[quote="panzer"]I generally will do simple wiring but today went to change a pendant light to a ceiling mounted one, I have three hefty black cables and a single grey one and three dark green earths.
The wiring colours are pretty random in this house circa 1955!
I guess i need to put these into a junction box and would use a 20 amp due to the size of the wires with a 1.5 mm flex going to the light.
Q1 which is live and neutral in the old wiring
Q2 is it ok to put the junction box in the ceiling void ( fixed to joist )
Q3 is junction box and flex size ok
Advice gratefully received[/quote]
yes 20 amp jumction box and 1.5 mm2 flex ok ( I always use heat resistant flex ).
your neutrals ( black wires ) go together in 1 terminal on its own.
the blue of the flex which is light neutral goes with these blacks also.
you switch wire which is connected to the lamp flex terminal of the the old ceiling rose would be red or Black with a red tag.
this is connected to the brown wire light switch live into a separate
the remaining reds are permanent lives and are connected into a separate
terminal , of the joint box.
all your green wires , and green yellow of light would be connected
together in separate terminal.
i would have an electrician check your connections and wiring for verification of earthing, because your wiring sounds dated and might need
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!