Can anyone help me???
I put up a new ceiling light in the lounge, keeping very close to the original holes but I appear to have done something wrong!
I only have lights in half the house and all the trips are on.
What else can I check? Is this going to cost me?????!
Thanks in advance to anyone who can help
how many wires are there? should be in most cases 3 reds/browns looped together not connected to the fitting itself (L in, L out to next light, L to switch)
also 2 Neutrals (Black or blue) connected to fitting N. (N in, N to next fitting),
Finally 1 odd wire from switch which is to L of fitting (should be red or brown , but may be black/blue if bad leckie fitted it cos it should have been taped/sleeved to show sw. live)
If still unsure there is a project with drawings on forum,
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!