I have a double 2 way switch. One of the switches operates, together with an upstairs switch,the light on the landing.Works perfectly well. The other switch is installed as an off/on control for two wall lights in the downstairs entrance hallway. It used to work. I can not remember if more work has been done in the house in that area but I do know it does not operate correctly now. When I use L1 and the common as the terminals the lights stay on permanently, When I use L2 and the common the lights will not work at all. A bathroom fitter happened to be in my house one day and mentioned that he had served his time as an electrician and confidently said that I had lost the neutral. He did not have the time to expand on that and was gone. Was he right and if so what does he mean and how do I correct the problem. I would be grateful for any advice on this matter. Regards Oldalex01
proptech wrote:Hi Oldalex01 The fact that you can get the lights to work indicates there is no neutral fault. Without any more info on your wiring, I would suggest you have a faulty switch.
Many thanks proptech.I will follow up your advice and replace the two gang switch. I did at one point swop the switches round with no change in the outcome. That is that the landing light worked perfectly well and the wall lights responded as before.
Thanks "proptech" you were spot on. I bought a new switch and bingo all the troubles were solved. I must say It crossed my mind that the trouble was with the switch but i discounted the Idea because it is such a simple component and it was manufactured by a very reputable company. Alls well that ends well though and thanks again. Regards Oldalex01
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!