Hi everyone, I installed a two way metal light switch, But everytime i switch on the power to the lights i get a small shock, not much more than around 6-12v, do you think it could be a defective switch, as all the cables a are correctly fitted (loose wires cause fires!) and there is no break in any of the cable's. thanks.
Years ago it was common not to run earth wires to lighting circuits. Although now earths are always run from time to time one finds one of these old installations the electrical safety council recommend a rewire in such cases but where the customer will not pay for rewire then all Class II fittings (i.e. Plastic) should be used plus notices should be fixed to the consumer unit warning of lack of earth and if they will not agree to this then electricians should refuse to work on the system.
Maybe you have one of these old systems and if so you should remove any metal light switches and replace with plastic.
However all is not lost there are some metal looking plastic covers that can be stuck to switches to make them look metal.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!