i have EDF comming yo move my meter on wednesday and the sparky i had comming has let me down
i have to move my fuse box across the house how far can it be from the meter ? can it be wired in by myself? are there any laws stopping me doing this ?
[quote="STEVEH"]i have EDF comming yo move my meter on wednesday and the sparky i had comming has let me down
i have to move my fuse box across the house how far can it be from the meter ? can it be wired in by myself? are there any laws stopping me doing this ?[/quote]
OK. THIS IS WHAT S KNOWN AS NOTIFIABLE WORK AND COMES
UNDER THE GOVERMENTS PART P REGULATIONS WHICH CAME
IN JAN 2005.
YES U COULD ATTEMPT THE WORK YOURSLEF , BUT U WOULD NEED TO NOTIFY LOCAL AUTHORITY BUILDING CONTROL.
THEY WOULD SEND SOMEONE ALONG TO CHECK THE WORK CONFORMED TO THIER BUILDING REGULATIONS.
BUT U WOULD STILL HAVE TO GET THE WORK TESTED AND A ELECTRICAL INSTALLATION CERTIFICATE ISSUED.
AN ELECTRICIAN COULD INSPECT AND TEST FOR U BUT HE COULD NOT ISSUE A ELECTRICAL INSTALLATION CERTIFICATE BECAUSE HE DID NOT
COMPLETE THE WORK.
WHAT HE WOULD DO IS CARRY A PERIODIC INSPECTION REPORT , AND
ISSUE THIS CERTIFICATE LISTING ANY REMEADIAL WORK REQUIRED.
LOCAL AUTHORITY BUILDING CONTROL WOULD CHARGE ANYTHING FROM Â£ 150 UPWARDS.
A PERIODIC INSPECTION COULD BE Â£ 100 . 00 APROX
SO TOTAL OFÂ£ 250 PLUS IF U GOT MAINS BOARD AND FITTED IT.
DEPENDING WHERE U R U MIGHT FIND IT BETTER TO GET A PART P
REGISTERED ELECTRICIAN , WHO IS ON ONE OF SLEF CERTIFICATION
SCHEMES , ECA , NAPPIT , NICEIC , WHO CAN REGISTER THE WORK DIRECT WITH THE LABC AND GIVE THE ELECTRICAL INSTALLATION CERTIFICATE TO U DIRECT.
IT COULD BE CHEAPER AS WELL
AS FOR HOW FAR FROM THE METER , A KMF SWITCH IS REQUTRED WHEN MORE THAN 2 METERS AWAY AND THE DISTANCE WOULD DEPEND ON MAXIMUM DEMAND CALCULATIONS TO WORK OUT SIZE OF MAIN
METER TAILS , WHICH WOULD INFLUENCE HOW FAR AWAY BOARD COULD BE. NORMALY 25 MM2 TAILS WOULD B LOOKED AT. A CALCULATION WOULD B DONE TO MEASURE MAX DISTANCE.
[quote="davidwm7650"]How far away from the intake position can the Consumer Unit be positioned?[/quote]
I am not aware of stated maximum distances , unless
local supply authority state a maximum distance from thier
a cable calculation would be needed to assess the size of main tails , once the postion of the mains board was relocated.
The sensible approach would be to relocate your mains
board the minimum distance , possible from present
location , if having to relocate.
If more than 2 meters away from intake metering position
a kmf , isolation switch with appropiate main fuse ( depending on size of tails ) would b required.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!