My appartment (in France) has only one socket with an earth...!
Let me explain in more detail..
I have just bought an appartment in Lourdes (France) The appartment is everything I expected, but there is a slight problem..
Only one socket in the appartment has an earth wire, it is in the bedroom, I want to be able to use appliances that require an earth terminal (Fridge/Kettle/Iron/Toaster) but it is not realistic to use them in the bedroom!
A neighbour said he got round the problem by running a wire from the waterpipe in the kitchen to the two nearest sockets (His dad did it for Him) but is this safe??
I have looked and there is a yellow and green wire from the copper water pipes to the two sockets.
I hope someone can help and sorry if this reflects something already posted before, I did look first.
Dont know about france , but here you could not use the water pipe, in a fault you may liven up all the pipework etc, possible you may just need a proper earth rod installed and tested,but I would check with someone qualified on french regs.
WE do bond pipework here but only to keep it at same voltage potential as earth, but this is in addition to the main electric supply earth being adequate, whether it by cable or earth rod.
The appartment is on the (7th) top floor, there is an earth in the bedroom socket, and one in the bedroom light fitting, can one of these be extended to an near by socket? I have some 4mm (5 core) earth wire.. is this any good?
I see an earth rod is a bit of a problem then,do you know if there is an earthing terminal or bar,where the main fuse supply enters the building.
Any bonds would be better going to that temporary, rather than a water pipe or having none at the sockets.
Not sure about france but our earths would be run with or within in the cable for each circuit, and its not acceptable to use an earth from another circuit, when inside this cable the earth core is never larger than the live cores ,so you may need some wiring done to conform.
Are you sure there is no earth, in some countries, sometimes sockets look two pin but have a metal earth tag which connects to the plug when inserted.
I would get someone qualified in france ,as if your freind has used water pipe ,it may possibly be ok to do this in france, or he may be putting the whole block at risk.
can you tell where the earth wires from bedroom go back to,to establish whether you have a supply earth.
Can you see green/yellow wires in the location of the supply.
Have you established the earth is suitable in the bedroom,as although the earthcore is present it possibly may not go back to the source.
As france use radial circuits someone may have just extended to the second socket using three core earthed cable from an existing twin wired unearthed socket ,there would then be one earth wire present in each but not functioning
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!