after a little bit of help if possible we have moved into a brand new house and have just come round to changing the light fittings from the standard buld on a wire. I have bought new light fittings for the kitchen and managed to change one like for like and it works. I have gone to change the other one and have 2 earth, 1 blue, 2 brown 1 black and 1 grey. I have a new light fitting which only has earth, brown and blue wires on a 3 set teminal (Box with tiny screws in). What shold I be onnecting to what? Please help!!!
Do you have another form of equipment other than the light to this circuit ie a fan.
If so you should have two types of cabling that are in grey plastic outer protection.
One set (three core and earth) with a black a grey and a brown plus the bare earth
they other (twin core and earth) should have a brown a blue and the earth.
All earth connected at the earth terminal on fitting or ceiling rose.
The twin core wires go blue to neutral side of fitting, the brown to loop in middle of rose.
The three core wires go as so grey in to loop, brown to live side of fitting and black to neutral.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!