[quote="rambo77"]hi there im fitting new double sockets into my conservatory spuring from an exsiting sock in my living room.. do the steel back boxes need to be earth or the face socket itselfs or both ???
U CAN ONLY SPUR FROM THE EXISTING SOCKET IN THE LIVING
ROOM IF THIS SOCKET IS ON THE RING MAIN . AND THE NUMBER OF SOCKETS U COULD HAVE IS
ONLY 1 DOUBLE OR 2 SINGLES . IF YOUR FACE PLATE SOCKETS ARE METAL THEN AN EARTH WOULD B CONNECTED TO FACEPLATE EARTH
TERMINAL AND METAL BACK BOX TERMINAL.
Hi Rambo; under the regulations; you cannot spur off of a spur (Except where a single socket is being added from an existing spurred single socket), you can only take a spur from the ring - You would need to add the living room socket to the main ring and then spur off of it.
Provision of a switched fused spur is not an accepted practice.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!