Hi, I need to remove a towel radiator so I can redecorate my bathroom. We have a combi boiler and I'm not sure whether I have to completely drain the system (and how exactly?), or can just bleed the radiator without touching anything else? Anybody have any tips on this.
Also I'll probably not be reattaching the radiator for quite some time and would therefore need to fill up the system again, so would it be a case of just shutting off the valves in the bathroom to stop it leaking and the system will run as normal? Sorry for the stupid questions, I have read up as much as I can but hoped someone here might be able to advise on this specific problem.
hi mully79 you can turn off both valves and just drain the rad u want to remove but with valves being attached to bottom it can be quite messy probably easiest to just drain top half of system to do that turn off the boiler make sure water has cooled down if heating has been used and attach a hose to a downstairs rad with a drainoff fitted then go round all rads on the upstairs level and any level above (if for example rads fitted in attic)and slightly open bleed valves then wait for water to stop running from hose then u are free to remove bathroom rad but remember u will hav to top up your boiler back to around 1 bar before you switch it back on hope this helps bazza
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!