Hi guys ..My ancient Primatic hot water cylinder sprung a leak and I replaced it with an indirect cylinder...trouble is the central heating doesnt work anymore....do I need to add another F&E tank to the system ( the old system just had 1 feed tank) if I need to add another feed tank where do I connect it to the new indirect cylinder ? please also be aware i'm a total novice at plumbing :lol:
you have just created a time bomb so do not turn on the boiler as there is now no expansion to the system the expansion tank should go in the roof with a cold feed and an expansion pipe over the tank
anyway you should not be fitting the repacement cyld yourself as it comes under the building regs notification scheme so only a competent person IE corgi engineer is classed as such so he can self certificate
i think you will see on the side of the new cyld there is such a notice that should be filled in
Ime afraid its all down to regulations these days gone are the days when d i y could do anything
"anyway you should not be fitting the repacement cyld yourself as it comes under the building regs notification scheme so only a competent person IE corgi engineer is classed as such so he can self certificate"
Thats not so. You only have to be registrered for unvented with a G3 ticket. For vented if you employ an Insitutue Of Plumbing member you do not need to involve Building Control. He doesn't need to be CORGI (Gas Safe from 1 April).
You CAN do it yourself but you DO need to involve Building Control.
Last edited by rosebery on Wed Feb 18, 2009 3:38 pm, edited 1 time in total.