i have a Ferroli F30 boiler and i need to replace the pump. the pump currently fitted is a Grundfos UPS 15 - 50, part number 59965505. i have searched everywhere for an identical pump but cant find one. does anyone know wheich pump i need to get to replace my current one?
Beware:- Not all UPS 15/50 are the same, some boiler manufacturers have some very strange base's (the part where the boiler pipe work connects to the pump) to stop you from picking up a straight replacement from a plumbers merchant and depriving them of revenue as they want to sell you spare parts. One way (but not always) of getting around this is to just use the motor part of the new pump and swap that for the old one. You will see the motor screws on the top, just release them and swap. However beware here again, carefully check that the pump impellers are the same size and or configeration as many boiler manufacturers have pump heads designed to suit the specific requirements of the boiler. Can be a bit of a minefield so it's up to you if you wish to risk it or not.
Thanks for your help. Ive had the pump changed but my boiler is still causing the same problem as before. I have hot water but when i turn the heating on, it works fine for about a minute, then in makes a spluttering noise and shuts off.
A friend has told me the problem may be with the thermostatic control valve?
Anybody have any ideas?
Yes it could be the diverter valve, but unlikely as it is moving over to allow heating, then the boiler cuts out. Could be the temperature thermister or control thermostat, could even be a fault on one of the PCB's. Best bet is to either talk to Ferolli technical help line or call out a CORGI engineer.