Wonder if someone can help, in my conversatory I had alight suspended from the celing, which was wired into a spur from the main circuit suppling the double sockets out there. The roof has been replaced and the lighting removed right back to the 5amp fuse. My question is how do i go about replacing the lighting circuit. Is it simply one length of cable to the light then onto the switch? If i wanted to mount 2 wall lights how do i progress, I read the adding a wall light project which states you need an exisiting cable that is not going to a switch, which I dont have unless I have the wrong end of the stick??
Any help greatly appreciated!!
at the fused spur is live, neutral & earth, if it is in the right position to use & is switched type, you only need run twin& earth to light & you'r done. however if not switched fused spur or in wrong place then run from spur to switch position, then on to light, connect neutrals together in switch box also connect earths together in box, then connect live to switch & switched live from switch, IE you are just looping thro N & E breaking L.
to fit additional wall lights simply connect cables N-N & E-E in switch box & fit double switch in place of single, put out going lives to wall lights in one L1 & centre light live to other L1 loop live in to both Common terms. in switches.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!