I am trying to replace my mechanical thermostat with a programmable one to enable me to time when the boiler goes on and off etc.
I am replacing a Robus RRF10 thermostat with the wiring as follows
2 Live (brown)
3 Neutral (grey)
5 Live linked across to 2
6 Black wire (not sure what it is)
I am trying to replace with a Danfoss TP5000M Si and to begin the wiring looked simple to replace however now it makes no sense to me as a novice. page 4 at http://danfoss-randall.co.uk/PCMPDF/082.pdf shows how it should be wired, using what i have above i used the brown and grey as live and neutral into the relevent L and N to the right with no remote input. what i put on the other side to NC COM and NO i think is where i am going wrong - i have tried live to the NC and the black wire to NO but still nothing is working - can anyone advise correct wiring ??
Assuming you have the 240v version you will need to put a link from the L terminal to the COM terminal and connect the black wire to the NO terminal. Since the instructions do not specify whether NO or NC is active with a fall in temperature you may have to swap the black lead onto the NC terminal (if the heating goes off when the temp is too low). Don't forget you will need to have the controller switched to continuous.
Now the trick thing is where does the grey wire (which is not a neutral) go? I would normally connect it to pin 1, the NC so when the temperature reaches the limit the contacts will open switching off the heat but the instructions say use pin 3 - NO????
Connect the grey to pin 1 and if the heat comes on when you turn the stat down, swap it to pin 3.
Another point, if you have a timer fitted, it needs setting to 24hrs otherwise the programmable stat may lose its settings as it should really have a permanent power supply.
Just a point as you have tried several combinations of wiring ensure no fuses have blown and the supply is live.
plumbbob - i am a little confused when you say that the grey wire that i have is a switched live to the boiler as the diagram on the back of the rrf10 shows this to be neutral into pin 3
wish i had never started this now - i made the assumption that it was simple to change the thermostat, now facing the prospect of potentially making a bang and ruining the thermostat - maybe best just to swallow pride and get someone in
Looks like you had better get a specialist in.
You have told us that you have 2-live, 3-neutral, on the existing controller.
Taking plumbbob's pin listing for 3 as being switched live (not neutral) the existing controller should have already gone bang.
Please get someone in to identify the existing wiring.
Sorry, your identification of the grey wire on terminal 3 of your existing controller as being neutral threw me.
Following plumbbob's warning your existing wiring is 1 unused, 2 live -brown, 3 switched live - grey, 4 unused, 5 neon (with link to 3), 6 neutral - black.
The new thermostat should be wired A neutral - black, B live - brown, link from B to 2 (COM), 1 NC - grey. Again you may need to swap grey onto 3 NO if the thermostat works the wrong way round.
Thanks to plumbbob for the warning.
Well I have done as you suggested stoneyboy and thought I had it cracked, thermostat powered up and I set time/date and programmes and left it to it and all seemed well but then it started clicking like it was switching on and off. On closer inspection it seems to do this when it reaches temperature and should be telling the boiler to stop. As stoneyboy suggested if the thermostat works the wrong way I tried it with the switch live (grey) into NO instead of NC however the thermostat did not power up when I did this
I would have expected the programmer to work with the grey wire fitted onto the NO terminal. If it worked with the grey wire onto NC changing it onto NO should not stop the programmer powering up. Check that the L and N connections are OK and that the wires are not broken.
I assume you did fit a wire link from LIVE to COM.
Have a look at the web page you gave a link to in your first post, are all the dip switches set as shown on page 2? Correct them if necessary and push the reset button this will reset the programmer to its factory set status.
The wires going to NC NO and Com should have no effect on the controller - it should power up with nothing on these terminals. Try the controller with just L N and E (if there is a terminal for E) connected it should display its settings. If it does not then you do need to check it is getting power - has the main controller turned heating off? Has the fuse blown?
If it does not work with only L and N connected (to L and N terminals) you will have to return it as a faulty unit.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!