hi guys. i have to fit a timer fan on a ceiling above a shower, the height of the ceiling is 2.35m from floor. do i have to fit a selv fan?
if so, a normal timer fan has a perminant live & a switched live at it. on a selv fan, which do i put through the isolating tansformer?
17th Edn has dispensed with Zone 3. Zone 1 still extends to 225mm above the floor for a bath/shower. At 2.35m you are outside the zones and can fit what you want as long as it conforms to the appropriate IP rating.
If its a new circuit then its notifiable and should be done by a qualified electrician. All circuits in a bathroom now have to be protected by a 30mA RCD. If its a like for like replacement you are OK on notification but its a moot point as to whether an MWC is required.
Are you fitting it in your own bathroom or are you doing it for someone else - presumably for some sort of remuneration ("I have to fit"). If its the latter and you need to ask the question about the iso tfr then perhaps you shouldn't be fitting it to be frank.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!