Hi there... this is my first post so please forgive me if this thread is in the wrong place.
Anyway, my problem is... My downstairs toilet is hooked up to a Saniflow unit which takes all the waste into the main sewage pipe. When I flush the downstairs loo I get a horrible sewage smell coming from the upstairs shower drain??
Can anyone tell me why this would be happening? It was fine for a few years and has only just started to happen so I don't think it's to do with the drain set up on the shower.
It is definitely to do with the drain set up.
Either, the water is being syphoned out of the trap by the vacuum created when the saniflo switches on, or you have a 'continental' style outlet from the shower which has no trap as such, or there is a blockage in the soil vent pipe.
I found a site which explains this if you
and also explains how you can stop the problem.
I used the HepVo dry trap on my shower ( had to cut a hole in the downstairs ceiling to fit it - but it was worth it!) and it worked a treat! No more having to keep the en-suite door shut to stop the stink coming into the bedroom at night. My shower was the 'easy-plumb' continental type outlet drain.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!