We have a holiday cottage that has 2 bedrooms with ensuite wet room style showers, wash basin & wc, and an open plan lounge and dining kitchen area.
Our problem is that when the wash basins or the sink in the kitchen drain water, they create a vacuum and suck the water out of the shower water traps. This allows foul smells back up into the shower.
A builder has told us that we need to separate completely our bedroom and kitchen basins from our showers that would involve a lot of new plumbing. Another plumber has suggested that if we install anti vac traps on the water basins that this might solve it.
I’d really welcome some advice as a novice in the plumbing world!
I attach two pictures that show the type of shower water traps that we have.
Is it both basins that cause the trap to be pulled out?
Shower trap will be very shallow and difficult to replace /alter.
Anti vac traps to the whb's will only prevent the traps to those basins being pulled. Fitting an anti vac trap to the shower will stop this being pulled.
Can you fit an air admittance valve (aav) between the whb's and the shower at some point. This could be a small 50mm aav but when the whb's are drained, air will be drawn into the system through the aav rather than sucking the shower trap out.
Mant thanks for your help on this one. So, do you mean that fitting anti-vac traps on the sinks won't stop the shower water traps being pulled? All that is on the pipe is 2 shower and basin traps, a kitchen basin & a dish washer. Also the smell we get only seems to impact one of the shower traps so I think only one of them is being pulled out completely.
Just to say a big thank you for your advice. We have had 3 air admittance valves fitted and it has solved the problem. The water is no longer sucked out of the shower traps & hence there is no smell. Brilliant. Many thanks.