[quote="Shane"]Hi . can you help. Have two double sockets one on each side of a gas cooker,both 90mm away.
A fused switch 70 mm from the edge of the sink.
A normal double socket under the sink almost underneath the top of the outlet of a dishwasher. ( 60mm from plug to side of vertical pipe )
My P reg man says this is all OK.
?? Where do I go from here ??[/quote]
SOCKETS SHOULD B AT LEAST 300 MM2 FROM COOKER AND
300 MM2 FOR FUSED SWITCH FROM EDGE OF SINK.
INFO FROM GUIDANCE NOTE 1 IEE SELECTION AND ERECTION OF EQUIPMENT.
AS 4 THE DOUBLE SOCKET I WOULD ASSUME IT WAS ON THE RING AND NOT A SPUR. AND IT BEING SO CLOSE TO THE OUTLET OF THE DISHWASHER IT SHOULD BE A WATERPROOF TYPE WITH SNAP SHUT COVER OVER PLUG.( I INSTALL THESE TYPE WITH LOW LEVEL WATER FED APPLIANCES, EG WASHING MACHINES DISHWASHERS , AND THEY R NORMALY FED FROM WORKTOP LEVEL SPURS ON THE RING , AND TO FEED THE APPLIANCE A SINGLE SOCKET FOR IT NOT DOUBLE )
I CANNOT COMMENT ON WHAT YOUR P REG MAN HAS DONE
BUT AS A PART P MAN MYSLEF THE COMMENTS I HAVE STATED IS HOW I WOULD INSTALL IT.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!