Hi all. I've re-run all my cold supplies from the mains because I'm taking out the storage tanks from the loft. I've re-used some pipes that were already in place under florboards and behind walls etc. How can I do a propper soundness test of my new c/w system: I dont mind buying necessary equipment as long as it isn't to industrial and expensive. Also do I need to flush the system in any way?. Thank you so much, in advance.
Yes, remove the pump, fit a loop in its place, do a visual check first, connections are ALL tight, in-line valves the correct way around, air vents closed, pressure test ~ 1 1/2 times max working pressure or 3bar ~ whicever is the greater, for 1 hour, with no drop (1%), snag the issues.
flush the system, its your time ~ so mayby twice, if ok, fill the system, bleed the rads, check for leaks, drain down the system, reinstall the pump, refil, check for leaks, check the F&E for corrcet level, heat the system, and flush while hot. add corrosion protection.
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!