I have a 13 amp. fused connection unit. This is fed from a socket which is on a radial circuit.(load on this is 100 watt)
I want to take a spur from this to feed another fcu which will feed an outside light. (load will be 300 watt)
I know that regs. do not allow me to take a spur from a spur , but as the total current is controlled by the first fcu, is this ok.
Hi Techmad, I can't see a problem; as you say the total load on overall spur can only be 13A , I have run from a FCU at 13A to a couple of sockets in a conservatory, then run up to a switched FCU with 3A fuse to control lights there,
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!