I am wiring up an Intermatic T101 Mechanical time switch to automate my pool lights. I raplaced an existing outdoor light switch. I have identified the load and line wires. The load wires are the standard black (hot), white (neutral) and green. The line wires are from a GFCI outlet and there are 4: White (N), Orange (N), yellow (hot), green. 110 volts passes yellow to orange and yellow to white, 0 volts white to orange. I don't know what to do with the extra neutral wire. I have attached the wiring diagram for the switch. Any help is appreciated! thanks.
Link deleted. No external links allowed.