I have drawn a diagram (Below). I am trying to get 2 lights working. 1 works on a single pole switch & the other is a dimmer. The pole switch has 3 wires going into it.2 white & 1 red. With the dimmer there are 2 wires. 1 black & 1 white. The switch was already wired so i shouldnt have to touch that. The problem im having is with the boxes in the ceiling. If i wire all the blacks together and all the whites together the lights come on but neither switch works. The 2nd box was all the blacks wired together & all the whites wired together. The 1st box for some reason originally had 3 blacks & 1 white (inclu. the black from the light) connected & three whites & one black connected. I cant remember which ones went where though&every combo i have tried hasnt worked so far. The left and right pairs of box 1 control the lights i think as when wired together both lights work. The trip blows if i add the other 2 wires in any combo.
I'd tested the wires with my volt meter to quickly find the switched wires that should be connected to the light fixtures. I noticed that the voltmeter is a must for doing electrical work. It need not be expensive or fancy. Thanks to the electrician!!! :lol:
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!