Hi, from what you say you have it must be old single core wiring in conduits, with lives looped at switches, neutrals looped at roses & switch wires in yellow. The sw. wires should have been over-sleeved red.
This practice was used in local authority housing a few years back, you will find the green earth wire comes from a terminal in back of conduit box, using conduit as earth continuity conductor (CPC). If this is so then you will have a metal consumer unit to pick up conduit earths.
If this is not so please reply with any other observations.
The loops are exactly as you describe and it is a local authority house...the use of the yellow cable was throwing me as I'd never seen it before and neither had a more experienced sparky I spoke to.
I'd have to do more investigation into the source of the earths but I do know that the consumer unit is a modern plastic one....MK I think.
Since my original post I have had a closer look at some of the wiring and have told my parents to get the council to have a look at it as I have found some live wiring cut off and tucked into skirting boards, and light fittings being back-fed from another source.
Glad it ain't my house but my mum is crapping herself now!!!
DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!