Warning: To complete electrical works you must comply with Electrical Regulations - Click here for more information.
Fans with an integral timer need a 3 core and earth supply to allow the unit to run on after a light is switched off. It must also be possible to isolate the fan by means of a pull switch inside the bathroom, or a fan isolation (3 pole) switch outside of the bathroom.
Before attempting fan or any other electrical connection ensure all circuits are off.
Isolation switch must be on a pull cord inside a bathroom or as above a switch on the outside.
- D = Earth Connection = To all units…This wire should be sleeved in a green/yellow earth sleeve.
- C = Neutral Connection = To 3 & 6
- A = Permanent Live Connection = To 2 & 5
- B = Switched Live Connection = To 1 & 4
For regulations governing heights of sockets etc, please see our Socket Height project page.
You might be interested to go to our video section on installing ceiling fans to watch a film on "ceiling fan installation".