# 13 Amp cable

Hi, am I correct in saying that I can run appliances rated at 1800W using 13A cable? The cable length will be approx 10 metres. My calculations give a current of about 8.2A working on a mains voltage of 220V.

Thanks 8)
meddyliol
Rank: Labourer
Progress to next rank:
50%
Posts: 3
Joined: Mon Apr 21, 2008 9:42 am

Sponsor

I would assume you mean 1.25mmÂ² flexible cords which will have 37 mV/A/m volt drop 1800W at 230 volt = 7.82 amps = 2.89 volts drop over 10 meters or 0.37 ohms all of which falls within the parameters laid out in both 16th and 17th edition and the code of practice for in-service inspection and testing of electrical equipment so yes you were correct in what you said. The only slight thing is we work on 230 volts as norm not 220 volts assuming you live in Europe. Although I have compared with UK harmonised rules with Europe. I assume you wish to prove to someone else which is why I include calculations.
ericmark

Thanks for your reply. I do not know why I used 220V instead of 230V, must be because I'm Welsh. Anyway, you have answered my question, I was just concerned about the safety factor really.

Thanks again

Brian
meddyliol
Rank: Labourer
Progress to next rank:
50%
Posts: 3
Joined: Mon Apr 21, 2008 9:42 am

Cumru Am Byth
ericmark

Display posts from previous
Sort by
Order by

• DIY How to Project Guides
• DIY how to tutorial projects and guides - Did you know we have a DIY Projects section? Well, if no, then we certainly do! Within this area of our site have literally hundreds of how-to guides and tutorials that cover a huge range of home improvement tasks. Each page also comes with pictures and a video to make completing those jobs even easier!

• Related Topics